ENUM_AD_MULTI_TENANT_NO:
  address: '0x0025'
  arithmetic: ''
  description: WiFi Kit Multi Tenant No.
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_2WAY_VALVE:
  address: '0x408A'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'CV'
    0x03: 'BOILER'
  remarks: 0 Off, 2 CV, 3 Boiler
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_3WAY_VALVE_2:
  address: '0x4113'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  enum:
    0x00: 'ROOM'
    0x01: 'TANK'
  type: ENUM
  unit: ''
ENUM_IN_BACKUP_HEATER:
  address: '0x406C'
  arithmetic: ''
  description: Backup heater mode
  enum:
    0x00: 'OFF'
    0x01: 'STEP 1'
    0x02: 'STEP 2'
  remarks: 0 Off, 1 Step 1, 2 Step 2
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_BOOSTER_HEATER:
  address: '0x4087'
  arithmetic: ''
  description: Booster heater
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: 0 Off, 1 On
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_CHILLER_EXT_WATER_OUT_INPUT:
  address: '0x4101'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_CHILLER_SETTING_DEMAND_LEVEL:
  address: '0x40FC'
  arithmetic: ''
  description: ''
  enum:
    0x00: '100 %'
    0x01: '95 %'
    0x02: '90 %'
    0x03: '85 %'
    0x04: '80 %'
    0x05: '75 %'
    0x06: '70 %'
    0x07: '65 %'
    0x08: '60 %'
    0x09: '55 %'
    0x0A: '50 %'
    0x0B: 'Not Apply'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_CHILLER_WATERLAW_ON_OFF:
  address: '0x40F7'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  type: ENUM
  unit: ''
ENUM_IN_CHILLER_WATERLAW_SENSOR:
  address: '0x40E7'
  arithmetic: ''
  description: DMV Chiller Option
  enum:
    0x00: 'OUTDOOR'
    0x01: 'ROOM'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_CHILLLER_SETTING_SILENT_LEVEL:
  address: '0x40FB'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'NONE'
    0x01: 'LEVEL 1'
    0x02: 'LEVEL 2'
    0x03: 'LEVEL 3'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_DIFFUSER_OPERATION_POWER:
  address: '0x4149'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_ENTER_ROOM_CONTROL_USED:
  address: '0x40D5'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'DISABLE'
    0x01: 'ENABLE'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_ENTHALPY_CONTROL_STATE:
  address: '0x4105'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_ERROR_HISTORY_CLEAR_FOR_HASS:
  address: '0x40D6'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FAN_MODE_REAL:
  address: '0x4007'
  arithmetic: ''
  description: Indoor unit current air volume
  enum:
    0x01: 'LOW'
    0x02: 'MID'
    0x03: 'HIGH'
    0x04: 'TURBO'
    0x0A: 'AUTOLOW'
    0x0B: 'AUTOMID'
    0x0C: 'AUTOHIGH'
    0x0D: 'UL'
    0x0E: 'LL'
    0x0F: 'HH'
    0x10: 'SPEED'
    0x11: 'NATURALLOW'
    0x12: 'NATURALMID'
    0x13: 'NATURALHIGH'
    0xFE: 'OFF'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
enum:
  0x00: 'OFF'
  0x01: 'ON'
  address: '0x410D'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_2041:
  address: '0x4093'
  arithmetic: ''
  description: Heating - Heating WL Selection WL Type
  enum:
    0x00: 'Unknown'
    0x01: 'Floor'
    0x02: 'FCU'
  remarks: 1 Floor, 2 FCU
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_2081:
  address: '0x4094'
  arithmetic: ''
  description: Cooling - Cooling WL Selection WL Type
  enum:
    0x00: 'Unknown'
    0x01: 'Floor'
    0x02: 'FCU'
  remarks: 1 Floor, 2 FCU
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_2093:
  address: '0x4127'
  arithmetic: ''
  description: Remote Controller - Remote Controller Room Temp. Control
  enum:
    0x01: 'Off (1min delay) by Room Sensor'
    0x02: 'Off (1min delay) by Room Sensor or WL'
    0x03: 'On'
    0x04: 'Repeat 3min On/7min Off by Room Sensor or WL'
  remarks: Min = 1 Max = 4
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_2094:
  address: '0x412A'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'no'
    0x01: 'one'
    0x02: 'two'
    0x03: 'three'
    0x04: 'four'
    0xFF: 'off'
  remarks: values 0="No" up to 4="4"
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_3041:
  address: '0x4099'
  arithmetic: ''
  description: DHW - Disinfection Application
  enum:
    0x00: 'Off'
    0x01: 'on'
  remarks: 0 No, 1 Yes
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_3042:
  address: '0x409A'
  arithmetic: ''
  description: DHW - Disinfection Interval
  enum:
    0x00: 'Sunday'
    0x01: 'Monday'
    0x02: 'Tuesday'
    0x03: 'Wednesday'
    0x04: 'Thursday'
    0x05: 'Friday'
    0x06: 'Saturday'
    0x07: 'Everyday'
  remarks: Sunday=0, Monday=1 .. up to 7=Everyday
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_3051:
  address: '0x409B'
  arithmetic: ''
  description: DHW - Forced DHW Operation Timer OFF Function
  enum:
    0x00: 'No'
    0x01: 'Yes'
  remarks: 0 No, 1 Yes
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_3071:
  address: '0x409D'
  arithmetic: ''
  description: DHW - Direction of  3Way Valve DHW Tank
  enum:
    0x00: 'Room'
    0x01: 'Tank'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_4011:
  address: '0x409E'
  arithmetic: ''
  description: Heating - Heat Pump Heating/ DHW Priority
  enum:
    0x00: 'DHW'
    0x01: 'Heating'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_4021:
  address: '0x409F'
  arithmetic: ''
  description: Heating - Backup Heater Application
  enum:
    0x00: 'No'
    0x01: '2 Step BUH1+BUH2'
    0x02: '1 Step BUH2'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_4022:
  address: '0x40A0'
  arithmetic: ''
  description: Heating - Backup Heater BUH/BSH Priority
  enum:
    0x00: 'BUH_BSH_Both'
    0x01: 'BUH'
    0x02: 'BSH'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_4023:
  address: '0x40A1'
  arithmetic: ''
  description: Heating - Backup Heater Cold Weather Compensation
  enum:
    0x00: 'No'
    0x01: 'Yes'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_4031:
  address: '0x40A2'
  arithmetic: ''
  description: Heating - Backup Boiler Application
  enum:
    0x00: 'No'
    0x01: 'Yes'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_4032:
  address: '0x40A3'
  arithmetic: ''
  description: Heating - Backup Boiler Priority
  enum:
    0x00: 'No'
    0x01: 'Yes'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_4041:
  address: '0x40C0'
  arithmetic: ''
  description: Heating - Mixing Valve Application
  enum:
    0x00: 'No'
    0x01: 'FSV_TARGET_DELTA'
    0x02: 'WL'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_4044:
  address: '0x40C1'
  arithmetic: ''
  description: Heating - Mixing Valve Control Factor
  enum:
    0x01: '1'
    0x02: '2'
    0x03: '3'
    0x04: '4'
    0x05: '5'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_4051:
  address: '0x40C2'
  arithmetic: ''
  description: Heating - Inverter Pump Application
  enum:
    0x00: 'No'
    0x01: '100%'
    0x02: '70%'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_4053:
  address: '0x40C3'
  arithmetic: ''
  description: Heating - Inverter Pump Control Factor
  enum:
    0x01: '1'
    0x02: '2'
    0x03: '3'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_4061:
  address: '0x411A'
  arithmetic: ''
  description: Heating - Zone Control Application
  enum:
    0x00: 'No'
    0x01: 'Yes'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_5022:
  address: '0x4128'
  arithmetic: ''
  description: DHW Saving - DHW Saving Mode 
  enum:
    0x00: 'ON'
    0x01: 'OFF'
  remarks: Min = 0 Max = 1
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_5033:
  address: '0x4107'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'A2A'
    0x01: 'DHW'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_5041:
  address: '0x40A4'
  arithmetic: ''
  description: Power Peak Control - Application
  enum:
    0x00: 'No'
    0x01: 'Yes'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_5042:
  address: '0x40A5'
  arithmetic: ''
  description: Power Peak Control - Select Forced Off Parts
  enum:
    0x00: 'COMP_PER_BUH_OFF_BSH_PER'
    0x01: 'COMP_PER_BUH_OFF_BSH_OFF'
    0x02: 'COMP_OFF_BUH_OFF_BSH_PER'
    0x03: 'COMP_OFF_BUH_OFF_BSH_OFF'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_5043:
  address: '0x40A6'
  arithmetic: ''
  description: Power Peak Control - Using Input Voltage
  enum:
    0x00: 'Low'
    0x01: 'High'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_5051:
  address: '0x40A7'
  arithmetic: ''
  description: Frequency Ratio Control
  enum:
    0x00: 'Disable'
    0x01: 'Use'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_5061:
  address: '0x40B4'
  arithmetic: ''
  description: 'Ratio of hot water supply compare to heating'
  enum:
    0x01: "1"
    0x02: "2"
    0x03: "3"
    0x04: "4"
    0x05: "5"
    0x06: "6"
    0x07: "7"
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_5081:
  address: '0x411B'
  arithmetic: ''
  description: PV Control - Application
  enum:
    0x00: 'No'
    0x01: 'Yes'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_5091:
  address: '0x411C'
  arithmetic: ''
  description: Smart Grid Control - Application
  enum:
    0x00: 'No'
    0x01: 'Yes'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_5094:
  address: '0x411D'
  arithmetic: ''
  description: Smart Grid Control - DHW Mode 
  enum:
    0x00: "55\u00b0 by HP"
    0x01: "70\u00b0 by HP and BSH"
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_LOAD_SAVE:
  address: '0x412D'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'min'
    0x01: 'max'
  remarks: Min = 0 Max = 1, similar name as 0x4125 in NASA.ptc
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_GAS_LEVEL:
  address: '0x4147'
  arithmetic: ''
  description: ''
  ernum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_LOUVER_HL_PART_SWING:
  address: '0x4012'
  arithmetic: ''
  description: Up and down wind direction setting/status
  enum:
    0x00: 'Sing_Off'
    0x01: 'LOUVER_1'
    0x02: 'LOUVER_2'
    0x03: 'LOUVER_1_2'
    0x04: 'LOUVER_3'
    0x05: 'LOUVER_1_3'
    0x06: 'LOUVER_2_3'
    0x07: 'LOUVER_1_2_3'
    0x08: 'LOUVER_4'
    0x09: 'LOUVER_1_4'
    0x0A: 'LOUVER_2_4'
    0x0B: 'LOUVER_1_2_4'
    0x0C: 'LOUVER_3_4'
    0x0D: 'LOUVER_1_3_4'
    0x0E: 'LOUVER_2_3_4'
    0x0F: 'Swing_On'
    0x40: 'H_H_H'
    0x41: 'M_H_H'
    0x42: 'V_H_H'
    0x44: 'H_M_H'
    0x45: 'M_M_H'
    0x46: 'V_M_H'
    0x48: 'H_V_H'
    0x49: 'M_V_H'
    0x4A: 'V_V_H'
    0x50: 'H_H_M'
    0x51: 'M_H_M'
    0x52: 'V_H_M'
    0x54: 'H_M_M'
    0x55: 'M_M_M'
    0x56: 'V_M_M'
    0x58: 'H_V_M'
    0x59: 'M_V_M'
    0x5A: 'V_V_M'
    0x60: 'H_H_V'
    0x61: 'M_H_V'
    0x62: 'V_H_V'
    0x64: 'H_M_V'
    0x65: 'M_M_V'
    0x66: 'V_M_V'
    0x68: 'H_V_V'
    0x69: 'M_V_V'
    0x6A: 'V_V_V'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_MTFC:
  address: '0x402F'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_OPERATION_POWER_ZONE1:
  address: '0x4119'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_OPERATION_POWER_ZONE2:
  address: '0x411E'
  arithmetic: ''
  description: Zone2 Normal Power
  enum:
    0x00: 'min'
    0x01: 'max'
  remarks: Min = 0 Max = 1
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_PV_CONTACT_STATE:
  address: '0x4123'
  arithmetic: ''
  description: PV Control
  enum:
    0x00: 'OFF'
    0x01: 'ON'
    0xFF: 'DISABLED'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_QUIET_MODE:
  address: '0x406E'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_ROOM_TEMP_SENSOR:
  address: '0x4076'
  arithmetic: ''
  enum:
    0x00: 'Idiom_IndoorUnit'
    0x01: 'Idiom_WiredRemocon'
  remarks: 'It tells the room sensor is present for zone #1 (EHS Mono R290 AE050CXYBEK).'
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_ROOM_TEMP_SENSOR_ZONE2:
  address: '0x4118'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'Idiom_IndoorUnit'
    0x01: 'Idiom_WiredRemocon'
  remarks: 'It tells the room sensor is present for zone #2 (EHS Mono R290 AE050CXYBEK).'
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_SG_READY_MODE_STATE:
  address: '0x4124'
  arithmetic: ''
  description: Smart Grid
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_STATE_AUTO_STATIC_PRESSURE_RUNNING:
  address: '0x40BB'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'Complete'
    0x02: 'Running'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_STATE_FLOW_CHECK:
  address: '0x4102'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_STATE_THERMO:
  address: '0x4028'
  arithmetic: ''
  description: Thermo On/Off
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: 0 Off, 1 On
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_STATE_WATER_PUMP:
  address: '0x4089'
  arithmetic: ''
  description: Water pump
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: 0 Off, 1 On
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_TDM_INDOOR_TYPE:
  address: '0x4108'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'A2A'
    0x01: 'A2W'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_THERMOSTAT1:
  address: '0x4069'
  arithmetic: ''
  description: Hydro_ExternalThermostat
  enum:
    0x00: 'OFF'
    0x01: 'Cool'
    0x02: 'Heat'
  remarks: 0 Off, 1 Cool, 2 Heat
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_THERMOSTAT2:
  address: '0x406A'
  arithmetic: ''
  description: Hydro_ExternalThermostat2
  enum:
    0x00: 'OFF'
    0x01: 'Cool'
    0x02: 'Heat'
  remarks: 0 Off, 1 Cool, 2 Heat
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_THERMOSTAT_WATER_HEATER:
  address: '0x40C5'
  arithmetic: ''
  description: Hydro_WaterHeaterThermostat
  enumy:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_WATERPUMP_PWM_VALUE:
  address: '0x40C4'
  arithmetic: ''
  description: Water pump speed
  remarks: "unit\xC2\_%"
  signed: ''
  type: VAR
  unit: '%'
ENUM_IN_WATER_VALVE_1_ON_OFF:
  address: '0x4103'
  arithmetic: ''
  description: FCU Kit
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_WATER_VALVE_2_ON_OFF:
  address: '0x4104'
  arithmetic: ''
  description: ''
  remarks: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_CHECK_REF_RESULT:
  address: '0x809C'
  arithmetic: ''
  description: Refrigerant amount determination result
  enum:
    0x00: 'RefResult_NotInspect'
    0x01: 'Normal_Completion'
    0x02: 'RefResult_NotJudgment'
    0x03: 'Unable_To_Secure_Supercooling'
    0x04: 'RefResult_Normal'
    0x05: 'RefResult_Insufficient'
    0x06: 'Judgment_Not_Possible'
    0x07: 'Temperature_Range_Exceeded'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_CONTROL_FAN_NUM:
  address: '0x8099'
  arithmetic: ''
  description: Number of outdoor fans
  remarks: ''
  signed: 'false'
  type: ENUM
  unit: ''
ENUM_OUT_EHS_WATEROUT_TYPE:
  address: '0x80D8'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'Default'
    0x01: '70 %'
  remarks: "0 Default, 1 70\xC2\xB0C"
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_INSTALL_ODU_COUNT:
  address: '0x8092'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: 'false'
  type: ENUM
  unit: ''
ENUM_OUT_LOAD_A2A_VALVE:
  address: '0x80C1'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_LOAD_OIL_BYPASS1:
  address: '0x80B8'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_LOAD_OIL_BYPASS2:
  address: '0x80B9'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_LOAD_PHEHEATER:
  address: '0x80D7'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_MCU_LOAD_COOL_A:
  address: '0x8049'
  arithmetic: ''
  description: MCU
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_MCU_LOAD_COOL_B:
  address: '0x804B'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_MCU_LOAD_COOL_C:
  address: '0x804D'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_MCU_LOAD_COOL_D:
  address: '0x804F'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_MCU_LOAD_COOL_E:
  address: '0x8051'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_MCU_LOAD_COOL_F:
  address: '0x8053'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_MCU_LOAD_HEAT_A:
  address: '0x804A'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_MCU_LOAD_HEAT_B:
  address: '0x804C'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_MCU_LOAD_HEAT_C:
  address: '0x804E'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_MCU_LOAD_HEAT_D:
  address: '0x8050'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_MCU_LOAD_HEAT_E:
  address: '0x8052'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_MCU_LOAD_HEAT_F:
  address: '0x8054'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_MCU_LOAD_LIQUID:
  address: '0x8055'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_MCU_PORT0_INDOOR_ADDR:
  address: '0x8058'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_MCU_PORT1_INDOOR_ADDR:
  address: '0x8059'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_MCU_PORT2_INDOOR_ADDR:
  address: '0x805A'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_MCU_PORT3_INDOOR_ADDR:
  address: '0x805B'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_MCU_PORT4_INDOOR_ADDR:
  address: '0x805C'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_MCU_PORT5_INDOOR_ADDR:
  address: '0x805D'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_OPERATION_AUTO_INSPECT_STEP:
  address: '0x803C'
  arithmetic: ''
  description: Automatic check step
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_OPERATION_SERVICE_OP:
  address: '0x8000'
  arithmetic: ''
  description: Indoor unit service operation steps
  enum:
    0x00: 'OFF'
    0x02: 'Heating_Test_Run'
    0x03: 'Pump_Out'
    0x0D: 'Cooling_Test_Run'
    0x0E: 'Pump_Down'
  remarks: 2 Heating test run, 3 Pump out, 13 Cooling test run, 14 Pump down
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_OP_A2_CURRENTMODE:
  address: '0x80BE'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'Null'
    0x01: 'A2W'
    0x02: 'A2A'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_OUT_OP_CHECK_REF_STEP:
  address: '0x808E'
  arithmetic: value & 0x0F
  description: Refrigerant amount level
  remarks: This is Enum in definition. But we need operation, so just consider this
    as variable. Min = 0, Max = 8
  enum:
    0x00: 'RefStep_0'
    0x01: 'RefStep_1'
    0x02: 'RefStep_2'
    0x03: 'RefStep_3'
    0x04: 'RefStep_4'
    0x05: 'RefStep_5'
    0x06: 'RefStep_6'
    0x07: 'RefStep_7'
    0x08: 'RefStep_8'
    0xFF: 'off'
  signed: 'false'
  type: ENUM
  unit: ''
ENUM_OUT_STATE_ACCUM_VALVE_ONOFF:
  address: '0x80B4'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
LVAR_AD_MCU_PORT_SETUP:
  address: '0x0448'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: LVAR
  unit: ''
LVAR_IN_AUTO_STATIC_PRESSURE:
  address: '0x4415'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: LVAR
  unit: ''
LVAR_IN_DEVICE_STAUS_HEATPUMP_BOILER:
  address: '0x440A'
  arithmetic: (value & 0x00000002) / 2
  description: Switch_HyrdoFlow
  remarks: ''
  signed: 'false'
  type: LVAR
  unit: ''
LVAR_IN_ENTER_ROOM_CONTROL_DATA:
  address: '0x441B'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: LVAR
  unit: ''
LVAR_IN_ETO_COOL_CONTROL_DATA:
  address: '0x441F'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: LVAR
  unit: ''
LVAR_IN_ETO_HEAT_CONTROL_DATA:
  address: '0x4420'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: LVAR
  unit: ''
LVAR_IN_MINUTES_SINCE_INSTALLATION:
  address: '0x4423'
  arithmetic: ''
  description: Minutes since installation
  remarks: 
  state_class: total_increasing
  device_class: duration
  signed: 'false'
  type: LVAR
  unit: 'min'
LVAR_IN_MINUTES_ACTIVE:
  address: '0x4424'
  arithmetic: ''
  description: Minutes active
  remarks: 
  state_class: total_increasing
  device_class: duration
  signed: 'false'
  type: LVAR
  unit: 'min'
LVAR_IN_GENERATED_POWER_LAST_MINUTE:
  address: '0x4426'
  arithmetic: value / 1000
  description: Generated power last minute
  remarks: value is kWh, so do div 1000
  device_class: energy
  signed: 'false'
  type: LVAR
  unit: kWh
LVAR_IN_TOTAL_GENERATED_POWER:
  address: '0x4427'
  arithmetic: value / 1000
  description: Total generated power
  remarks: value is kWh, so do div 1000
  state_class: total_increasing
  device_class: energy
  signed: 'false'
  type: LVAR
  unit: kWh
LVAR_OUT_AUTO_INSPECT_RESULT0:
  address: '0x840B'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: LVAR
  unit: ''
LVAR_OUT_AUTO_INSPECT_RESULT1:
  address: '0x840C'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: LVAR
  unit: ''
NASA_ADDRESSING:
  address: '0x2003'
  arithmetic: ''
  description: ''
  remarks: seen in NASA data from EHS Mono HT Quiet
  signed: ''
  type: ''
  unit: ''
NASA_ADDRESSING_ASSIGN_CONFIRM_ADDRESS:
  address: '0x2002'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_AHUPANEL_AHUKIT_ADDRESS:
  address: '0x461C'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: STR
  unit: ''
NASA_AHUPANEL_CO2_CONTROL:
  address: '0x40CA'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_AHUPANEL_DUTY_CONTROL:
  address: '0x40C8'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_AHUPANEL_EA_RATE:
  address: '0x4294'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_AHUPANEL_ENERGYMANAGE_CONTROL:
  address: '0x40CB'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_AHUPANEL_ENTHALPY_CONTROL:
  address: '0x40C7'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_AHUPANEL_ERROR_STATUS:
  address: '0x40CF'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_AHUPANEL_HEATER_ONOFF_STATUS:
  address: '0x40D0'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_AHUPANEL_MIXING_RATE:
  address: '0x429B'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_AHUPANEL_MIXING_TEMP:
  address: '0x429A'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_AHUPANEL_OA_DAMPER_TARGET_RATE:
  address: '0x4291'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_AHUPANEL_OA_HUMIDITY:
  address: '0x4296'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_AHUPANEL_OA_TEMP:
  address: '0x4295'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_AHUPANEL_PANEL_OPTION:
  address: '0x461D'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: STR
  unit: ''
NASA_AHUPANEL_POINT_STATUS:
  address: '0x429C'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_AHUPANEL_RA_FAN_ONOFF_STATUS:
  address: '0x40CE'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_AHUPANEL_RA_HUMIDITY:
  address: '0x4293'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_AHUPANEL_RA_SMOKE_DECTION_STATUS:
  address: '0x40CC'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_AHUPANEL_RA_TEMP:
  address: '0x4292'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_AHUPANEL_SA_FAN_ONOFF_STATUS:
  address: '0x40D1'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_AHUPANEL_SA_FAN_STATUS:
  address: '0x40CD'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_AHUPANEL_SA_HUMIDITY:
  address: '0x4298'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: ''
NASA_AHUPANEL_SA_TEMP:
  address: '0x4297'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: ''
NASA_AHUPANEL_SMOKE_DECTION_CONTROL:
  address: '0x40D2'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_AHUPANEL_STATIC_PRESSURE:
  address: '0x4299'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_AHUPANEL_SUMMERNIGHT_CONTROL:
  address: '0x40C9'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_AHUPANEL_TARGET_HUMIDITY:
  address: '0x4290'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_AIRFLOW_LEFTRIGHT:
  address: '0x407E'
  arithmetic: ''
  description: Left and right wind direction settings/status
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: 0 Off, 1 On
  signed: ''
  type: ENUM
  unit: ''
NASA_AIRFLOW_UPDOWN:
  address: '0x4011'
  arithmetic: ''
  description: Up and down wind direction setting/status
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_ALL_LAYER_DEVICE_COUNT:
  address: '0x2400'
  arithmetic: ''
  description: ''
  remarks: seen in NASA data from EHS Mono HT Quiet
  signed: ''
  type: LVAR
  unit: ''
NASA_ALL_POWER_CONSUMPTION_CUMULATIVE:
  address: '0x0407'
  arithmetic: ''
  description: Total cumulative power consumption
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_ALL_POWER_CONSUMPTION_SET:
  address: '0x0406'
  arithmetic: ''
  description: Total instantaneous power consumption
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_ALL_REMOTE_LEVEL:
  address: '0x0409'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: LVAR
  unit: ''
NASA_ALTERNATIVE_MODE:
  address: '0x4060'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: 0 Off, 9 On
  signed: ''
  type: ENUM
  unit: ''
NASA_CHANGE_ALL_NETWORK_STATUS:
  address: '0x200A'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_CHANGE_CONTROL_NETWORK_STATUS:
  address: '0x2006'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_CHANGE_LOCAL_NETWORK_STATUS:
  address: '0x2008'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_CHANGE_MODULE_NETWORK_STATUS:
  address: '0x2009'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_CHANGE_POLAR:
  address: '0x2001'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_CHANGE_SET_NETWORK_STATUS:
  address: '0x2007'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_COMMU_MICOM_BUTTON:
  address: '0x2018'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_COMMU_MICOM_LED:
  address: '0x2017'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_CONFIRM_ADDRESS:
  address: '0x0401'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: LVAR
  unit: ''
NASA_CONTROL_AUTO_CLEAN:
  address: '0x4042'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_CONTROL_DESIRED_HUMIDITY:
  address: '0x405E'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_CONTROL_HUMIDIFICATION:
  address: '0x4041'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_CONTROL_MDS:
  address: '0x403F'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_CONTROL_OAINTAKE:
  address: '0x403D'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_CONTROL_OUTER_COOL:
  address: '0x405C'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_CONTROL_SILENCE:
  address: '0x4046'
  arithmetic: ''
  description: Silence mode
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: 0 Off, 1 On
  signed: ''
  type: ENUM
  unit: ''
NASA_CONTROL_SILENCT:
  address: '0x4050'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_CONTROL_SPI:
  address: '0x4043'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_COOL_SET_DISCHARGE:
  address: '0x422A'
  arithmetic: value / 10
  description: User limitation - Water Cooling Temperature Max.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_CURRENT_DISCHARGE:
  address: '0x420B'
  arithmetic: value / 10
  description: Indoor Discharge Temp(Duct, AHU)
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_CURRENT_TEMP:
  address: '0x4203'
  arithmetic: value / 10
  description: Room Temperature
  remarks: 'Room temperature for zone #1'
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_CYCLEOPTION:
  address: '0x0603'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: STR
  unit: ''
NASA_DEMAND_SYNC_TIME:
  address: '0x0213'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_DETECTION_TYPE:
  address: '0x000D'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
VAR_IN_FSV_1051:
  address: '0x4252'
  arithmetic: value / 10
  description: User limitation - Hot Water Temperature Max.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_1052:
  address: '0x4253'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_DHW_OPMODE:
  address: '0x4066'
  arithmetic: ''
  description: Water heater mode
  enum:
    0x00: 'Eco'
    0x01: 'Standard'
    0x02: 'Power'
    0x03: 'Force'
  remarks: 0 Eco, 1 Standard, 2 Power, 3 Force
  signed: ''
  type: ENUM
  unit: ''
NASA_DHW_OPMODE_SUPPORT:
  address: '0x40B1'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_DHW_POWER:
  address: '0x4065'
  arithmetic: ''
  description: Water heater power
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: 0 Off, 1 On
  signed: ''
  type: ENUM
  unit: ''
NASA_DHW_REFERENCE_TEMP:
  address: '0x406F'
  arithmetic: ''
  description: Hydro_ControlChoice_RoomTemp
  enum:
    0x00: 'ROOM'
    0x01: 'Water out'
  remarks: 0 Room, 1 Water out. Variable isEhsSetTempWaterOut. See 0x4201 and 0x4247.
  signed: ''
  type: ENUM
  unit: ''
NASA_DHW_VALVE:
  address: '0x4067'
  arithmetic: ''
  description: Hydro_3Way
  enum:
    0x00: 'ROOM'
    0x01: 'TANK'
  remarks: 0 Room, 1 Tank
  signed: ''
  type: ENUM
  unit: ''
NASA_DISCHARGE_TEMP_ENABLE:
  address: '0x4070'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: '0 Off, 1 On (rem: "DISCHAGE" is typo in NASA.ptc)'
  signed: ''
  type: ENUM
  unit: ''
NASA_EEPROM_CODE:
  address: '0x060C'
  arithmetic: ''
  description: OutdoorTableEEPROMDBCodeVersion
  remarks: ''
  signed: ''
  type: STR
  unit: ''
NASA_EHS_FSV_SETTING_MIN_MAX_TEMP:
  address: '0x461A'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: STR
  unit: ''
NASA_EHS_INDOOR_OPMODE:
  address: '0x4064'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_EHS_INDOOR_POWER:
  address: '0x4063'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_EHS_SETTING_MIN_MAX_TEMP:
  address: '0x4619'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: STR
  unit: ''
NASA_ENABLEDOWNLOAD:
  address: '0x000A'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
ENUM_IN_FSV_3011:
  address: '0x4097'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'No'
    0x01: 'one'
    0x02: 'two'
  remarks: values 0="No" up to 2="2"
  signed: ''
  type: ENUM
  unit: ''
NASA_ERROR_CODE1:
  address: '0x0202'
  arithmetic: ''
  description: Error code
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
NASA_ERROR_CODE2:
  address: '0x0203'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_ERROR_CODE3:
  address: '0x0204'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_ERROR_CODE4:
  address: '0x0205'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_ERROR_CODE5:
  address: '0x0206'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_ERROR_INOUT:
  address: '0x440F'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: LVAR
  unit: ''
NASA_ERV_FANSPEED:
  address: '0x4008'
  arithmetic: ''
  description: Indoor unit current air volume
  enum:
    0x00: 'Auto'
    0x01: 'Low'
    0x02: 'Mid'
    0x03: 'High'
    0x04: 'Turbo'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_ERV_OPMODE:
  address: '0x4004'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  enum:
    0x00: 'Normal'
    0x01: 'HeatEx'
    0x02: 'Bypass'
    0x03: 'Normal_Purify'
    0x04: 'HeatEx_Purify'
    0x05: 'Purify'
    0x06: 'Sleep'
    0x07: 'Bypass_Purify'
  type: ENUM
  unit: ''
NASA_ERV_POWER:
  address: '0x4003'
  arithmetic: ''
  description: Ventilation operation mode
  remarks: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  signed: ''
  type: ENUM
  unit: ''
NASA_EVA_INHOLE_TEMP:
  address: '0x4208'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_EVA_IN_TEMP:
  address: '0x4205'
  arithmetic: value / 10
  description: Indoor Eva In Temperature
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_EVA_OUT_TEMP:
  address: '0x4206'
  arithmetic: value / 10
  description: Indoor Eva Out Temperature
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_FANSPEED:
  address: '0x4006'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_FILTER_CLEAN:
  address: '0x4025'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_FILTER_WARNING:
  address: '0x4027'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  type: ENUM
  unit: ''
NASA_GATHER_INFORMATION:
  address: '0x0007'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_GATHER_INFORMATION_COUNT:
  address: '0x0008'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_GROUPCONTROL_BIT1:
  address: '0x4405'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_GROUPCONTROL_BIT2:
  address: '0x4406'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_GROUPCONTROL_BIT3:
  address: '0x4407'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_HEAT_SET_DISCHARGE:
  address: '0x422B'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_HUMIDITY_PERCENT:
  address: '0x4038'
  arithmetic: ''
  description: ''
  remarks: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  signed: ''
  type: ENUM
  unit: ''
NASA_IM_MASTER:
  address: '0x2000'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_IM_MASTER_NOTIFY:
  address: '0x0000'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_INDOOR_ABLE_FUNCTION:
  address: '0x4604'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: STR
  unit: ''
NASA_INDOOR_ABSOLUTE_CAPACITY:
  address: '0x4212'
  arithmetic: value / 8.5
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: kW
NASA_INDOOR_AIRCLEANFAN_CURRENT_RPM:
  address: '0x4220'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: 'rpm'
NASA_INDOOR_CAPACITY:
  address: '0x4211'
  arithmetic: value / 8.5
  description: Capacity
  remarks: ''
  signed: 'false'
  type: VAR
  unit: kW
VAR_IN_FSV_1021:
  address: '0x424C'
  arithmetic: value / 10
  description: User limitation - Room Cooling Temperature Max.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_1011:
  address: '0x424A'
  arithmetic: value / 10
  description: User limitation - Water Cooling Temperature Max.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_1022:
  address: '0x424D'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_1012:
  address: '0x424B'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_INDOOR_CURRENT_EEV2:
  address: '0x4218'
  arithmetic: ''
  description: Current EEV2 development level
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
NASA_INDOOR_CURRENT_EEV3:
  address: '0x4219'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_INDOOR_CURRENT_EEV4:
  address: '0x421A'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_INDOOR_DEFROST_STATUS:
  address: '0x402E'
  arithmetic: ''
  description: Defrost mode
  remarks: 0 Off, 1 On
  signed: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  type: ENUM
  unit: ''
NASA_INDOOR_DHW_CURRENT_TEMP:
  address: '0x4237'
  arithmetic: value / 10
  description: DHW tank current temperature
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_INDOOR_DHW_SET_TEMP:
  address: '0x4235'
  arithmetic: value / 10
  description: DHW target temperature
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_1041:
  address: '0x4250'
  arithmetic: value / 10
  description: User limitation - Room heating Temperature Max.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_1031:
  address: '0x424E'
  arithmetic: value / 10
  description: User limitation - Water Heating Temperature Max.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_1042:
  address: '0x4251'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_1032:
  address: '0x424F'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_INDOOR_MODEL_INFORMATION:
  address: '0x4229'
  arithmetic: ''
  description: Indoor unit model information
  remarks: ''
  signed: ''
  type: VAR
  unit: ''
NASA_INDOOR_OPMODE:
  address: '0x4001'
  arithmetic: ''
  description: Indoor unit control mode
  enum:
    0x00: 'Auto'
    0x01: 'Cool'
    0x02: 'Dry'
    0x03: 'Fan'
    0x04: 'Heat'
    0x15: 'Cool Storage'
    0x18: 'Hot water'
  remarks: 0 Auto, 1 Cool, 2 Dry, 3 Fan, 4 Heat, 21 Cool Storage, 24 Hot water
  signed: ''
  type: ENUM
  unit: ''
NASA_INDOOR_OUTER_TEMP:
  address: '0x420C'
  arithmetic: value / 10
  description: ''
  remarks: same value as 0x8204 (sensor_airout) ?
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_INDOOR_OUT_GOING:
  address: '0x406D'
  arithmetic: ''
  description: Outing mode
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: 0 Off, 1 On
  signed: ''
  type: ENUM
  unit: ''
NASA_INDOOR_POWER_CONSUMPTION:
  address: '0x4284'
  arithmetic: ''
  description: Indoor unit power consumption
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_INDOOR_REAL_OPMODE:
  address: '0x4002'
  arithmetic: ''
  description: Indoor unit current operation mode
  enum:
    0x00: 'Auto'
    0x01: 'Cool'
    0x02: 'Dry'
    0x03: 'Fan'
    0x04: 'Heat'
    0x0B: 'Auto Cool'
    0x0C: 'Auto Dry'
    0x0D: 'Auto Fan'
    0x0E: 'Auto Heat'
    0x15: 'Cool Storage'
    0x18: 'Hot water'
    0xFF: 'NULL mode'
  remarks: 0 Auto, 1 Cool, 2 Dry, 3 Fan, 4 Heat, 11 Auto Cool, 12 Auto Dry, 13 Auto
    Fan, 14 Auto Heat, 21 Cool Storage, 24 Hot water, 255 NULL mode
  signed: ''
  type: ENUM
  unit: ''
NASA_INDOOR_SETTEMP_WATEROUT:
  address: '0x4247'
  arithmetic: value / 10
  description: Hydro_WaterOutletTargetF
  remarks: variable waterOutSetTemp
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_INDOOR_SETTING_MIN_MAX_TEMP:
  address: '0x4608'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: STR
  unit: ''
NASA_INDOOR_WATER_IN_TEMP:
  address: '0x4236'
  arithmetic: value / 10
  description: Hydro_WaterIn
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_INDOOR_WATER_OUT_TEMP:
  address: '0x4238'
  arithmetic: value / 10
  description: Hydro_WaterOut
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_INODDR_CURRENT_EEV1:
  address: '0x4217'
  arithmetic: ''
  description: Current EEV development level
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
NASA_INSPECTION_MODE:
  address: '0x0004'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_INSTALLOPTION2:
  address: '0x0602'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: STR
  unit: ''
NASA_INSTALL_OPTION:
  address: '0x0601'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: STR
  unit: ''
NASA_LAYER:
  address: '0x200F'
  arithmetic: ''
  description: Enumeration Type
  remarks: ''
  signed: ''
  enumy:
    0x00: 'Control_Layer'
    0x01: 'Set_Layer'
  type: ENUM
  unit: ''
NASA_LEVEL_AIRSWING:
  address: '0x040D'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: LVAR
  unit: ''
NASA_LEVEL_COOL_HIGH_TEMP_LIMIT:
  address: '0x0411'
  arithmetic: (value & 0xFFFF0000u) >> 16) / 10.0
  description: ''
  remarks: ''
  signed: 'false'
  type: LVAR
  unit: "\u00b0C"
NASA_LEVEL_COOL_LOW_TEMP_LIMIT:
  address: '0x0412'
  arithmetic: (value & 0xFFFF0000u) >> 16) / 10.0
  description: ''
  remarks: ''
  signed: 'false'
  type: LVAR
  unit: "\u00b0C"
NASA_LEVEL_FANSPEED:
  address: '0x040C'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: LVAR
  unit: ''
NASA_LEVEL_HEAT_HIGH_TEMP_LIMIT:
  address: '0x0413'
  arithmetic: (value & 0xFFFF0000u) >> 16) / 10.0
  description: ''
  remarks: ''
  signed: 'false'
  type: LVAR
  unit: "\u00b0C"
NASA_LEVEL_HEAT_LOW_TEMP_LIMIT:
  address: '0x0414'
  arithmetic: (value & 0xFFFF0000u) >> 16) / 10.0
  description: ''
  remarks: ''
  signed: 'false'
  type: LVAR
  unit: "\u00b0C"
NASA_LEVEL_KEEP_ALTERNATIVE_MODE:
  address: '0x040F'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: LVAR
  unit: ''
NASA_LEVEL_KEY_INPUT:
  address: '0x0416'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: LVAR
  unit: ''
NASA_LEVEL_OPMODE:
  address: '0x040B'
  arithmetic: value & 0xFF
  description: ''
  remarks: ''
  signed: 'false'
  type: LVAR
  unit: ''
NASA_LEVEL_OPMODE_LIMIT:
  address: '0x0410'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: LVAR
  unit: ''
NASA_LEVEL_OUT_POINT_INPUT:
  address: '0x0415'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: LVAR
  unit: ''
NASA_LEVEL_POWER:
  address: '0x040A'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: LVAR
  unit: ''
NASA_LEVEL_SETTEMP:
  address: '0x040E'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: LVAR
  unit: ''
NASA_MICOM_CODE:
  address: '0x0608'
  arithmetic: ''
  description: OutdoorUnitMainDBCodeVersion
  remarks: VariableAssign Identifier="dbCode"
  signed: ''
  type: STR
  unit: ''
NASA_MODIFIED_CURRENT_TEMP:
  address: '0x4204'
  arithmetic: value / 10
  description: Temperature
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_NAME:
  address: '0x0605'
  arithmetic: ''
  description: ''
  remarks: appears when using S-NET pro 2 software
  signed: ''
  type: STR
  unit: ''
NASA_NET_ADDRESS:
  address: '0x0210'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_4WAY2_VALVE:
  address: '0x802A'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_4WAY_VALVE:
  address: '0x801A'
  arithmetic: ''
  description: 4Way On/Off
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_ACCUMULATOR_CCH:
  address: '0x8016'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_ACCUM_RETURN2_VALVE:
  address: '0x80AC'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_ACCUM_RETURN_VALVE:
  address: '0x8037'
  arithmetic: ''
  description: ARV On/Off
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_ACCUM_TEMP:
  address: '0x82C8'
  arithmetic: value / 10
  description: Accumulator outlet temperature
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_OUTDOOR_APPEARANCE_RPM:
  address: '0x82D0'
  arithmetic: value / 10
  description: Appearance RPM
  remarks: ''
  signed: 'false'
  type: VAR
  unit: rpm
NASA_OUTDOOR_BACKUP_OPERATION:
  address: '0x80A5'
  arithmetic: ''
  description: Backup operation operation status On/Off
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_BASE_HEATER:
  address: '0x80AF'
  arithmetic: ''
  description: Base heater On/Off state for EHS
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: 0 Off, 1 On
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_CBOX_COOLING_FAN:
  address: '0x809E'
  arithmetic: ''
  description: DC Fan
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_CBOX_TEMP:
  address: '0x82BE'
  arithmetic: value / 10
  description: Contor Box Temp
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_OUTDOOR_CCH1_STATUS:
  address: '0x8013'
  arithmetic: ''
  description: CCH1 On/Off
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_CCH2_STATUS:
  address: '0x8014'
  arithmetic: ''
  description: CCH2 On/Off
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_CCH3_STATUS:
  address: '0x8015'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_CH_SWITCH_VALUE:
  address: '0x80B2'
  arithmetic: ''
  description: ''
  remarks: seen in NASA data from EHS Mono HT Quiet
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_COMP1_ORDER_HZ:
  address: '0x8236'
  arithmetic: ''
  description: Instruction frequency 1
  remarks: ''
  signed: 'false'
  type: VAR
  unit: 'Hz'
NASA_OUTDOOR_COMP1_RUNNING_TIME:
  address: '0x8405'
  arithmetic: ''
  description: OutdoorTableCompressorRunningTime 1
  remarks: hours
  signed: 'false'
  type: LVAR
  unit: ''
NASA_OUTDOOR_COMP1_RUN_HZ:
  address: '0x8238'
  arithmetic: ''
  description: Current frequency 1
  remarks: ''
  signed: 'false'
  type: VAR
  unit: 'Hz'
NASA_OUTDOOR_COMP1_STATUS:
  address: '0x8010'
  arithmetic: ''
  description: Comp#1 On/Off
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_COMP1_TARGET_HZ:
  address: '0x8237'
  arithmetic: ''
  description: Target frequency 1
  remarks: ''
  signed: 'false'
  type: VAR
  unit: 'Hz'
NASA_OUTDOOR_COMP2_ORDER_HZ:
  address: '0x8274'
  arithmetic: ''
  description: Instruction frequency 2
  remarks: ''
  signed: 'false'
  type: VAR
  unit: 'Hz'
NASA_OUTDOOR_COMP2_RUNNING_TIME:
  address: '0x8406'
  arithmetic: ''
  description: OutdoorTableCompressorRunningTime 2
  remarks: ''
  signed: 'false'
  type: LVAR
  unit: ''
NASA_OUTDOOR_COMP2_RUN_HZ:
  address: '0x8276'
  arithmetic: ''
  description: Current frequency 2
  remarks: ''
  signed: 'false'
  type: VAR
  unit: 'Hz'
NASA_OUTDOOR_COMP2_STATUS:
  address: '0x8011'
  arithmetic: ''
  description: Comp#2 On/Off
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_COMP2_TARGET_HZ:
  address: '0x8275'
  arithmetic: ''
  description: Target frequency 2
  remarks: ''
  signed: 'false'
  type: VAR
  unit: 'Hz'
NASA_OUTDOOR_COMP3_ORDER_HZ:
  address: '0x82C0'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: 'Hz'
NASA_OUTDOOR_COMP3_RUNNING_TIME:
  address: '0x840E'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_COMP3_RUN_HZ:
  address: '0x82C2'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: 'Hz'
NASA_OUTDOOR_COMP3_STATUS:
  address: '0x8012'
  arithmetic: ''
  description: Comp#3 On/Off
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_COMP3_TARGET_HZ:
  address: '0x82C1'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: 'Hz'
NASA_OUTDOOR_COMPENSATE_COOL_CAPA:
  address: '0x829C'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_COMPENSATE_HEAT_CAPA:
  address: '0x829D'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_COM_PROTECT_OPERATIOIN:
  address: '0x80A6'
  arithmetic: ''
  description: Compressor protection control operation status On/Off
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: 0 Off, 1 On
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_COND_OUT1:
  address: '0x8218'
  arithmetic: value / 10
  description: Main heat exchanger outlet temperature
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_OUTDOOR_COND_OUT2:
  address: '0x82BF'
  arithmetic: value / 10
  description: Sub heat exchanger outlet temperature
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_OUTDOOR_COND_OVER_COOL:
  address: '0x82CE'
  arithmetic: value / 10
  description: Outdoor heat exchanger subcooling degree
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
NASA_OUTDOOR_CONTROL_PRIME_UNIT:
  address: '0x823F'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
NASA_OUTDOOR_CONTROL_WATTMETER_1UNIT:
  address: '0x8411'
  arithmetic: ''
  description: Instantaneous power consumption of outdoor unit. One outdoor unit.
    Not used by the controller.
  remarks: appears about every 135 seconds, so less often than 0x8413
  signed: ''
  type: LVAR
  unit: ''
NASA_OUTDOOR_CONTROL_WATTMETER_1UNIT_ACCUM:
  address: '0x8412'
  arithmetic: ''
  description: Cumulative power consumption of outdoor unit. One outdoor unit. Not
    used by the controller.
  remarks: never seen in NASA data from EHS Mono HT Quiet
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_CONTROL_WATTMETER_ALL_UNIT:
  address: '0x8413'
  arithmetic: value / 1000
  description: Outdoor unit instantaneous power consumption. Sum of modules
  remarks: appears about every 30 seconds, not once in a minute
  signed: 'false'
  type: LVAR
  unit: kW
NASA_OUTDOOR_CONTROL_WATTMETER_ALL_UNIT_ACCUM:
  address: '0x8414'
  arithmetic: value / 1000
  description: Outdoor unit cumulative power consumption. Sum of modules
  remarks: value is Wh, so do div 1000
  state_class: total_increasing
  device_class: energy
  signed: 'false'
  type: LVAR
  unit: kWh
NASA_OUTDOOR_CONTROL_WATTMETER_TOTAL_SUM:
  address: '0x8415'
  arithmetic: ''
  description: Total (indoor + outdoor) instantaneous power consumption
  remarks: never seen in NASA data from EHS Mono HT Quiet
  signed: ''
  type: LVAR
  unit: ''
NASA_OUTDOOR_CONTROL_WATTMETER_TOTAL_SUM_ACCUM:
  address: '0x8416'
  arithmetic: ''
  description: Total (indoor + outdoor) cumulative power consumption
  remarks: never seen in NASA data from EHS Mono HT Quiet
  signed: ''
  type: LVAR
  unit: ''
NASA_OUTDOOR_COOLONLY_MODEL:
  address: '0x809D'
  arithmetic: ''
  description: ''
  remarks: seen in NASA data from EHS Mono HT Quiet (value always = 0)
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_COOL_SUM_CAPA:
  address: '0x8298'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_CT1:
  address: '0x8217'
  arithmetic: value / 10
  description: Compressor 1 current
  remarks: very unprecise, just 1 fractional digit
  signed: 'false'
  type: VAR
  unit: ''
NASA_OUTDOOR_CT2:
  address: '0x8277'
  arithmetic: ''
  description: Compressor 2 current
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
NASA_OUTDOOR_CT3:
  address: '0x82A3'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_CT_RESTRICT_OPTION:
  address: '0x829B'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_DCLINK1_VOLT:
  address: '0x823B'
  arithmetic: ''
  description: DC Link1 (Inverter DC voltage input)
  remarks: Min 0, Max 1000
  signed: 'false'
  type: VAR
  unit: ''
NASA_OUTDOOR_DCLINK2_VOLT:
  address: '0x82B3'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_DCLINK3_VOLT:
  address: '0x82C3'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_DEFROST_STEP:
  address: '0x8247'
  arithmetic: ''
  description: Outdoor unit defrost operation steps
  enum:
    0x01: 'Defrost stage 1'
    0x02: 'Defrost stage 2'
    0x03: 'Defrost stage 3'
    0x04: 'Defrost stage 4'
    0x05: 'Defrost stage 5'
    0x06: 'Defrost stage 6'
    0x07: 'Defrost operation end stage'
    0x08: 'Defrost stage 8'
    0x09: 'Defrost stage 9'
    0xFF: 'No defrost operation'
  remarks: 1 Defrost stage 1, 2 Defrost stage 2, 3 Defrost stage 3, 4 Defrost stage
    4, 7 Defrost operation end stage, 255 No defrost operation
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_DISCHARGE_TEMP1:
  address: '0x820A'
  arithmetic: value / 10
  description: Discharge1
  remarks: The discharge temperature in a heat pump refers to the temperature of the
    refrigerant as it exits the compressor and enters the condenser.
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_OUTDOOR_DISCHARGE_TEMP2:
  address: '0x820C'
  arithmetic: value / 10
  description: Discharge2
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_OUTDOOR_DISCHARGE_TEMP3:
  address: '0x820E'
  arithmetic: value / 10
  description: Discharge3
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_OUTDOOR_DOUBLE_TUBE:
  address: '0x821C'
  arithmetic: value / 10
  description: Liquid pipe temperature
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_OUTDOOR_DRED_LEVEL:
  address: '0x80A7'
  arithmetic: ''
  description: ''
  remarks: seen in NASA data from EHS Mono HT Quiet
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_EHSCOUNT:
  address: '0x0209'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_ENGINE_RPM:
  address: '0x82CF'
  arithmetic: ''
  description: Engine RPM
  remarks: ''
  signed: 'false'
  type: VAR
  unit: 'rpm'
NASA_OUTDOOR_ENGINE_WATER_TEMP:
  address: '0x82C9'
  arithmetic: value / 10
  description: Engine water temperature
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_OUTDOOR_ERVCOUNT:
  address: '0x0208'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_EVA_IN:
  address: '0x82DE'
  arithmetic: value / 10
  description: Eva In for EHS
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_OUTDOOR_EVIEEV:
  address: '0x822E'
  arithmetic: ''
  description: EVI EEV
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
NASA_OUTDOOR_EVI_BYPASS_VALVE:
  address: '0x8021'
  arithmetic: ''
  description: EVI ByPass On/Off
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_EVI_IN:
  address: '0x821E'
  arithmetic: value / 10
  description: EVI IN
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_OUTDOOR_EVI_OUT:
  address: '0x8220'
  arithmetic: value / 10
  description: EVI OUT
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_OUTDOOR_EVI_SOL1_VALVE:
  address: '0x8022'
  arithmetic: ''
  description: EVI Sol1 On/Off
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_EVI_SOL2_VALVE:
  address: '0x8023'
  arithmetic: ''
  description: EVI Sol2 On/Off
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_EVI_SOL3_VALVE:
  address: '0x8024'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_EXT_CMD_OPERATION:
  address: '0x8081'
  arithmetic: ''
  description: ''
  remarks: seen in NASA data from EHS Mono HT Quiet
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_FAN_CT1:
  address: '0x82B9'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_FAN_CT2:
  address: '0x82BA'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_FAN_IPM1_TEMP:
  address: '0x82A6'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: "\u00b0C"
NASA_OUTDOOR_FAN_IPM2_TEMP:
  address: '0x82A7'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: "\u00b0C"
NASA_OUTDOOR_FAN_RPM1:
  address: '0x823D'
  arithmetic: ''
  description: Outdoor Fan1 RPM
  remarks: ''
  signed: 'false'
  type: VAR
  unit: 'rpm'
NASA_OUTDOOR_FAN_RPM2:
  address: '0x823E'
  arithmetic: ''
  description: Outdoor Fan2 RPM
  remarks: ''
  signed: 'false'
  type: VAR
  unit: 'rpm'
NASA_OUTDOOR_FAN_STEP1:
  address: '0x8226'
  arithmetic: ''
  description: Outdoor Fan Step
  remarks: Min 0, Max 10000
  signed: 'false'
  type: VAR
  unit: ''
NASA_OUTDOOR_FAN_STEP2:
  address: '0x8227'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: VAR
  unit: ''
NASA_OUTDOOR_FLOW_SWITCH:
  address: '0x803B'
  arithmetic: ''
  description: Flow Switch
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_FLUX_VARIABLE_VALVE:
  address: '0x82BD'
  arithmetic: ''
  description: Flow Control
  remarks: ''
  signed: 'true'
  type: VAR
  unit: ''
NASA_OUTDOOR_GAS_CHARGE:
  address: '0x8025'
  arithmetic: ''
  description: Hot Gas Chargin
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_HEATING_PERCENT:
  address: '0x8231'
  arithmetic: ''
  description: ''
  remarks: seen in NASA data from EHS Mono HT Quiet
  signed: ''
  type: VAR
  unit: ''
NASA_OUTDOOR_HIGH_PRESS:
  address: '0x8206'
  arithmetic: (value / 10) * 0.980665
  description: High pressure
  remarks: ''
  signed: 'true'
  type: VAR
  unit: bar
NASA_OUTDOOR_HIGH_PRESS_TEMP:
  address: '0x829F'
  arithmetic: value / 10
  description: High pressure saturation temperature
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_OUTDOOR_HOTGAS1:
  address: '0x8017'
  arithmetic: ''
  description: HotGas1 On/Off
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_HOTGAS2:
  address: '0x8018'
  arithmetic: ''
  description: HotGas2 On/Off
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_HP:
  address: '0x8287'
  arithmetic: 'value * 0.7457'
  description: Outdoor unit horsepower (in kw)
  remarks: unknown UNIT "HP"
  signed: 'false'
  type: VAR
  unit: kw
NASA_OUTDOOR_HREEV:
  address: '0x822F'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_INDOORCOUNT:
  address: '0x0207'
  arithmetic: ''
  description: Number of indoor units connected
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
NASA_OUTDOOR_INDOOR_DEFROST_STEP:
  address: '0x8061'
  arithmetic: ''
  description: Indoor unit defrost operation steps
  enum:
    0x01: 'Defrost stage 1'
    0x02: 'Defrost stage 2'
    0x03: 'Defrost stage 3'
    0x04: 'Defrost stage 4'
    0x07: 'Defrost operation end stage'
    0xFF: 'No defrost operation'
  remarks: 1 Defrost stage 1, 2 Defrost stage 2, 3 Defrost stage 3, 4 Defrost stage
    4, 7 Defrost operation end stage, 255 No defrost operation
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_IPM_TEMP1:
  address: '0x8254'
  arithmetic: value / 10
  description: IPM1 Temperature
  remarks: Min -41, Max 150. The IPM is a component within the inverter system. It
    is responsible for converting the incoming direct current (DC) power from the
    power supply into alternating current (AC) power that drives the compressor motor.
    The term "intelligent" is often used because the IPM includes sophisticated electronics
    and control algorithms that optimize the motor's performance.
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_OUTDOOR_IPM_TEMP2:
  address: '0x8255'
  arithmetic: value / 10
  description: IPM2 Temperature
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_OUTDOOR_IPM_TEMP3:
  address: '0x82C4'
  arithmetic: 'value / 10'
  description: 'IPM 3 Temperartur'
  remarks: ''
  signed: ''
  type: ''
  unit: "\u00b0C"
NASA_OUTDOOR_LIQUID_BYPASS_VALVE:
  address: '0x8019'
  arithmetic: ''
  description: Liquid On/Off
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_LIQUID_TUBE_VALVE:
  address: '0x8034'
  arithmetic: ''
  description: Liquid tube
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_LOADINGTIME:
  address: '0x8228'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_LOGICAL_DEFROST_STEP:
  address: '0x8062'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_LOW_PRESS:
  address: '0x8208'
  arithmetic: (value / 10) * 0.980665
  description: low pressure
  remarks: ''
  signed: 'true'
  type: VAR
  unit: bar
NASA_OUTDOOR_LOW_PRESS_TEMP:
  address: '0x82A0'
  arithmetic: value / 10
  description: Low pressure saturation temperature
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_OUTDOOR_MAINEEV1:
  address: '0x8229'
  arithmetic: ''
  description: Main EEV1
  remarks: "An Electronic Expansion Valve, or EEV for short, is\xC2\_installed before\
    \ the evaporator in an air handler/coil and after the condenser in a heat pump.\
    \ It regulates the refrigerant flow rate to control superheat at the evaporator\
    \ outlet by opening and closing."
  signed: 'false'
  type: VAR
  unit: ''
NASA_OUTDOOR_MAINEEV2:
  address: '0x822A'
  arithmetic: ''
  description: Main EEV2
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
NASA_OUTDOOR_MAINEEV3:
  address: '0x822B'
  arithmetic: ''
  description: Main EEV3
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
NASA_OUTDOOR_MAINEEV4:
  address: '0x822C'
  arithmetic: ''
  description: Main EEV4
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
NASA_OUTDOOR_MAINEEV5:
  address: '0x822D'
  arithmetic: ''
  description: Main EEV5
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
NASA_OUTDOOR_MAIN_COOL_VALVE:
  address: '0x801F'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_MCUCOUNT:
  address: '0x0211'
  arithmetic: ''
  description: Number of connected MCUs
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
NASA_OUTDOOR_MID_PRESS:
  address: '0x82B8'
  arithmetic: (value / 10) * 0.980665
  description: medium pressure
  remarks: ''
  signed: 'true'
  type: VAR
  unit: bar
NASA_OUTDOOR_MODELINFORMATION:
  address: '0x860D'
  arithmetic: ''
  description: Structure Type
  remarks: ''
  signed: ''
  type: STR
  unit: ''
NASA_OUTDOOR_OCT1:
  address: '0x8278'
  arithmetic: ''
  description: Compressor OCT1
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
NASA_OUTDOOR_OCT2:
  address: '0x8279'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_OCT3:
  address: '0x82A4'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_ODU_CAPA1:
  address: '0x8240'
  arithmetic: ''
  description: current electric capacity of outdoor unit
  remarks: value in percent, appears about every 140 seconds, not a reliable number
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_ODU_CAPA2:
  address: '0x8241'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_ODU_CAPA3:
  address: '0x827E'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_ODU_CAPA4:
  address: '0x827F'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_OD_EEV_VALVE:
  address: '0x8020'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_OIL_BALANCE_STEP:
  address: '0x8245'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_OIL_BYPASS_VALVE:
  address: '0x82CA'
  arithmetic: ''
  description: Oil Bypass Valve
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
NASA_OUTDOOR_OIL_RECOVERY_STEP:
  address: '0x8244'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_OLP_TEMP:
  address: '0x8222'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: VAR
  unit: "\u00b0C"
NASA_OUTDOOR_OPERATION_CAPA_SUM:
  address: '0x8233'
  arithmetic: value / 8.5
  description: ''
  remarks: "/ 8.6 (better 8.5\xC2\_?). Does NOT show nominal Power Capacity, instead\
    \ shows current ACTIVE Power Capacity"
  signed: ''
  type: VAR
  unit: 'kW'
NASA_OUTDOOR_OPERATION_MODE:
  address: '0x8003'
  arithmetic: ''
  description: Outdoor unit cooling/heating mode
  enum:
    0x00: 'Undefined'
    0x01: 'Cool'
    0x02: 'Heat'
    0x03: 'CoolMain'
    0x04: 'HeatMain'
  remarks: 0 Undefined, 1 Cool, 2 Heat, 3 CoolMain, 4 HeatMain
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_OPERATION_STATUS:
  address: '0x8001'
  arithmetic: ''
  description: Outdoor Driving Mode
  enum:
    0x00: 'OP_STOP'
    0x01: 'OP_SAFETY'
    0x02: 'OP_NORMAL'
    0x03: 'OP_BALANCE'
    0x04: 'OP_RECOVERY'
    0x05: 'OP_DEICE'
    0x06: 'OP_COMPDOWN'
    0x07: 'OP_PROHIBIT'
    0x08: 'OP_LINEJIG'
    0x09: 'OP_PCBJIG'
    0x0A: 'OP_TEST'
    0x0B: 'OP_CHARGE'
    0x0C: 'OP_PUMPDOWN'
    0x0D: 'OP_PUMPOUT'
    0x0E: 'OP_VACCUM'
    0x0F: 'OP_CALORYJIG'
    0x10: 'OP_PUMPDOWNSTOP'
    0x11: 'OP_SUBSTOP'
    0x12: 'OP_CHECKPIPE'
    0x13: 'OP_CHECKREF'
    0x14: 'OP_FPTJIG'
    0x15: 'OP_NONSTOP_HEAT_COOL_CHANGE'
    0x16: 'OP_AUTO_INSPECT'
    0x17: 'OP_ELECTRIC_DISCHARGE'
    0x18: 'OP_SPLIT_DEICE'
    0x19: 'OP_INVETER_CHECK'
    0x1A: 'OP_NONSTOP_DEICE'
    0x1B: 'OP_REM_TEST'
    0x1C: 'OP_RATING'
    0x1D: 'OP_PC_TEST'
    0x1E: 'OP_PUMPDOWN_THERMOOFF'
    0x1F: 'OP_3PHASE_TEST'
    0x20: 'OP_SMARTINSTALL_TEST'
    0x21: 'OP_DEICE_PERFORMANCE_TEST'
    0x22: 'OP_INVERTER_FAN_PBA_CHECK'
    0x23: 'OP_AUTO_PIPE_PAIRING'
    0x24: 'OP_AUTO_CHARGE'
  remarks: 0 OP_STOP, 1 OP_SAFETY, 2 OP_NORMAL, 3 OP_BALANCE, 4 OP_RECOVERY, 5 OP_DEICE,
    6 OP_COMPDOWN, 7 OP_PROHIBIT, 8 OP_LINEJIG, 9 OP_PCBJIG, 10 OP_TEST, 11 OP_CHARGE,
    12 OP_PUMPDOWN, 13 OP_PUMPOUT, 14 OP_VACCUM, 15 OP_CALORYJIG, 16 OP_PUMPDOWNSTOP,
    17 OP_SUBSTOP, 18 OP_CHECKPIPE, 19 OP_CHECKREF, 20 OP_FPTJIG, 21 OP_NONSTOP_HEAT_COOL_CHANGE,
    22 OP_AUTO_INSPECT, 23 OP_ELECTRIC_DISCHARGE, 24 OP_SPLIT_DEICE, 25 OP_INVETER_CHECK,
    26 OP_NONSTOP_DEICE, 27 OP_REM_TEST, 28 OP_RATING, 29 OP_PC_TEST, 30 OP_PUMPDOWN_THERMOOFF,
    31 OP_3PHASE_TEST, 32 OP_SMARTINSTALL_TEST, 33 OP_DEICE_PERFORMANCE_TEST, 34 OP_INVERTER_FAN_PBA_CHECK,
    35 OP_AUTO_PIPE_PAIRING, 36 OP_AUTO_CHARGE
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_OPMODELIMIT:
  address: '0x8066'
  arithmetic: ''
  description: ''
  remarks: seen in NASA data from EHS Mono HT Quiet
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_OPMODE_OPTION:
  address: '0x8200'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: VAR
  unit: ''
NASA_OUTDOOR_OUT_TEMP:
  address: '0x8204'
  arithmetic: value / 10
  description: Outdoor temperature
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_OUTDOOR_OVER_COOL:
  address: '0x82CD'
  arithmetic: ''
  description: Outdoor unit supercooling
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
NASA_OUTDOOR_PHASE_CURRENT:
  address: '0x82DB'
  arithmetic: ''
  description: Phase current value
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
NASA_OUTDOOR_PROJECT_CODE:
  address: '0x82BC'
  arithmetic: ''
  description: Project code
  remarks: ''
  signed: 'true'
  type: VAR
  unit: ''
NASA_OUTDOOR_PUMPOUT_VALVE:
  address: '0x8027'
  arithmetic: ''
  description: Pump Out
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_RUNNING_SUM_CAPA:
  address: '0x8230'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: VAR
  unit: ''
NASA_OUTDOOR_SAFETY_START:
  address: '0x8248'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: VAR
  unit: ''
NASA_OUTDOOR_SERVICEOPERATION:
  address: '0x8047'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_SETUP_INFO:
  address: '0x860F'
  arithmetic: ''
  description: Structure Type
  remarks: ''
  signed: ''
  type: STR
  unit: ''
NASA_OUTDOOR_SNOW_LEVEL:
  address: '0x82D3'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_SUBMICOM:
  address: '0x8601'
  arithmetic: ''
  description: Structure Type
  remarks: ''
  signed: ''
  type: STR
  unit: ''
NASA_OUTDOOR_SUB_COND_EEV_STEP:
  address: '0x82D2'
  arithmetic: ''
  description: Sub EEV
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
NASA_OUTDOOR_SUB_COND_OVER_HEAT:
  address: '0x82CC'
  arithmetic: value / 10
  description: Sub heat exchanger outlet superheat
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
NASA_OUTDOOR_SUCTION1_TEMP:
  address: '0x821A'
  arithmetic: value / 10
  description: Suction temperature
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_OUTDOOR_SUCTION2_TEMP:
  address: '0x829A'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_OUTDOOR_SUCTION_OVER_HEAT:
  address: '0x82CB'
  arithmetic: value / 10
  description: Suction superheat
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
NASA_OUTDOOR_SUMPTEMP:
  address: '0x8210'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: "\u00b0C"
NASA_OUTDOOR_SYSTEM_RESET:
  address: '0x8065'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_TARGET_DISCHARGE:
  address: '0x8223'
  arithmetic: value / 10
  description: Target discharge temperature
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_OUTDOOR_TEST_OP_COMPLETE:
  address: '0x8046'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_OUTDOOR_TOP_SENSOR_TEMP1:
  address: '0x8280'
  arithmetic: value / 10
  description: Top1
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_OUTDOOR_TOP_SENSOR_TEMP2:
  address: '0x8281'
  arithmetic: value / 10
  description: Top2
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_OUTDOOR_TOP_SENSOR_TEMP3:
  address: '0x8282'
  arithmetic: 'value / 10'
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: "\u00b0C"
NASA_OUTDOOR_TW1_TEMP:
  address: '0x82DF'
  arithmetic: value / 10
  description: Water In 1 for EHS
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_OUTDOOR_TW2_TEMP:
  address: '0x82E0'
  arithmetic: value / 10
  description: Water In 2 for EHS
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_OUTDOOR_UPL_TP_COOL:
  address: '0x82D5'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_UPL_TP_HEAT:
  address: '0x82D6'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_OUTDOOR_VARIABLE_SETUP_INFO:
  address: '0x8417'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: LVAR
  unit: ''
NASA_OUTDOOR_WATER_TEMP:
  address: '0x825E'
  arithmetic: value / 10
  description: Water Temperature
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_OUTDOOR_WATER_VALVE:
  address: '0x8026'
  arithmetic: ''
  description: 2Way Valve
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_PBAOPTION:
  address: '0x0604'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_PEAK_CONTROL_PERIOD:
  address: '0x0010'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_PEAK_CURRENT_DEMAND:
  address: '0x0444'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_PEAK_CURRENT_TARGET_DEMAND:
  address: '0x0437'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_PEAK_FORCAST_DEMAND:
  address: '0x0438'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_PEAK_LEVEL:
  address: '0x000E'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_PEAK_MODE:
  address: '0x000F'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_PEAK_RATIO_CURRENT:
  address: '0x0434'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_PEAK_RATIO_POTENTIAL:
  address: '0x0435'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_PEAK_REAL_VALUE:
  address: '0x0445'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_PEAK_SYNC_TIME:
  address: '0x0443'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_PEAK_TARGET_DEMAND:
  address: '0x0214'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_PEAK_TARGET_POWER:
  address: '0x043A'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_PEAK_TOP_DEMAND:
  address: '0x0439'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_PEAK_TOTAL_POWER:
  address: '0x0436'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_PNP:
  address: '0x2004'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_PNP_CONFIRM_ADDRESS:
  address: '0x0417'
  arithmetic: ''
  description: PNP only
  remarks: ''
  signed: ''
  type: LVAR
  unit: ''
NASA_PNP_NET_ADDRESS:
  address: '0x0217'
  arithmetic: ''
  description: PNP only
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_PNP_RANDOM_ADDRESS:
  address: '0x0418'
  arithmetic: ''
  description: PNP only
  remarks: ''
  signed: ''
  type: LVAR
  unit: ''
NASA_PNP_SETUP_ADDRESS:
  address: '0x0419'
  arithmetic: ''
  description: PNP only
  remarks: ''
  signed: ''
  type: LVAR
  unit: ''
NASA_POWER:
  address: '0x4000'
  arithmetic: ''
  description: Indoor unit power on/off
  enum:
    0x00: 'OFF'
    0x01: 'ON'
    0x02: 'On Alternate'
  remarks: 0 Off, 1 On, 2 On
  signed: ''
  type: ENUM
  unit: ''
NASA_POWER_CHANNEL1_ELECTRIC_VALUE:
  address: '0x041C'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL1_PULSEVALUE:
  address: '0x043B'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL1_TYPE:
  address: '0x0012'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL1_USED:
  address: '0x001A'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL2_ELECTRIC_VALUE:
  address: '0x041D'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL2_PULSEVALUE:
  address: '0x043C'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL2_TYPE:
  address: '0x0013'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL2_USED:
  address: '0x001B'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL3_ELECTRIC_VALUE:
  address: '0x041E'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL3_PULSEVALUE:
  address: '0x043D'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL3_TYPE:
  address: '0x0014'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL3_USED:
  address: '0x001C'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL4_ELECTRIC_VALUE:
  address: '0x041F'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL4_PULSEVALUE:
  address: '0x043E'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL4_TYPE:
  address: '0x0015'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL4_USED:
  address: '0x001D'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL5_ELECTRIC_VALUE:
  address: '0x0420'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL5_PULSEVALUE:
  address: '0x043F'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL5_TYPE:
  address: '0x0016'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL5_USED:
  address: '0x001E'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL6_ELECTRIC_VALUE:
  address: '0x0421'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL6_PULSEVALUE:
  address: '0x0440'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL6_TYPE:
  address: '0x0017'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL6_USED:
  address: '0x001F'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL7_ELECTRIC_VALUE:
  address: '0x0422'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL7_PULSEVALUE:
  address: '0x0441'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL7_TYPE:
  address: '0x0018'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL7_USED:
  address: '0x0020'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL8_ELECTRIC_VALUE:
  address: '0x0423'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL8_PULSEVALUE:
  address: '0x0442'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL8_TYPE:
  address: '0x0019'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_CHANNEL8_USED:
  address: '0x0021'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_POWER_MANUFACTURE:
  address: '0x0011'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_PRODUCT_MODEL_NAME:
  address: '0x061A'
  arithmetic: ''
  description: ''
  remarks: appears when using S-NET pro 2 software
  signed: ''
  type: STR
  unit: ''
NASA_PRODUCT_OPTION:
  address: '0x0600'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: STR
  unit: ''
NASA_RANDOM_ADDRESS:
  address: '0x0403'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_RMCADDRESS:
  address: '0x0402'
  arithmetic: ''
  description: ''
  remarks: LogicalAnd 0xFF
  signed: 'false'
  type: LVAR
  unit: ''
NASA_SERIAL_NO:
  address: '0x0607'
  arithmetic: ''
  description: OutdoorTableSerialNumber
  remarks: ''
  signed: ''
  type: STR
  unit: ''
NASA_SETUP_ADDRESS:
  address: '0x0408'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: LVAR
  unit: ''
NASA_SET_DISCHARGE:
  address: '0x4209'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_SET_TEMP:
  address: '0x4201'
  arithmetic: value / 10
  description: Indoor unit set temperature
  remarks: if isEhsSetTempWaterOut (406F) ==1 , use value of variable waterOutSetTemp
    = 4247
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_SIMPIM_PASSWORD:
  address: '0x0619'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_SIMPIM_SYNC_DATETIME:
  address: '0x0613'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_SMART_GRID:
  address: '0x406B'
  arithmetic: ''
  description: Smart Grid
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_SOLAR_PUMP:
  address: '0x4068'
  arithmetic: ''
  description: Hydro_SolarPump
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_STANDBY_MODE:
  address: '0x0023'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_TRACKING_RESULT:
  address: '0x2010'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_3031:
  address: '0x4098'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: 0 Off, 1 On
  signed: ''
  type: ENUM
  unit: ''
NASA_USE_CENTUAL_CONTROL:
  address: '0x401B'
  arithmetic: ''
  description: Income from InstallOption information.
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_USE_DESIRED_HUMIDITY:
  address: '0x405D'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
ENUM_IN_FSV_3061:
  address: '0x409C'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'No'
    0x01: 'one'
    0x02: 'two'
    0x03: 'three'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_USE_DISCHARGE_TEMP:
  address: '0x4019'
  arithmetic: 'value '
  description: This value is a value that cannot be controlled by the upper controller.
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ""
NASA_USE_FILTER_WARNING_TIME:
  address: '0x4024'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_USE_HUMIDIFICATION:
  address: '0x4040'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_USE_MDS:
  address: '0x403E'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_USE_OUTER_COOL:
  address: '0x405B'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_USE_SILENCE:
  address: '0x4045'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ''
  unit: ''
NASA_USE_SPI:
  address: '0x4023'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_2091:
  address: '0x4095'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'No'
    0x01: 'one'
    0x02: 'two'
    0x03: 'three'
    0x04: 'four'
  remarks: values 0="No" up to 4="4"
  signed: ''
  type: ENUM
  unit: ''
ENUM_IN_FSV_2092:
  address: '0x4096'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'No'
    0x01: 'one'
    0x02: 'two'
    0x03: 'three'
    0x04: 'four'
  remarks: values 0="No" up to 4="4"
  signed: ''
  type: ENUM
  unit: ''
NASA_USE_VACANCY_STATUS:
  address: '0x40BD'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_USE_WIREDREMOTE:
  address: '0x4018'
  arithmetic: ''
  description: ''
  enum:
    0x00: 'OFF'
    0x01: 'ON'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
NASA_VACANCY_SETTING:
  address: '0x4418'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: LVAR
  unit: ''
NASA_VACANCY_STATUS:
  address: '0x40BC'
  arithmetic: ''
  description: Vacancy control
  enum:
    0x00: 'Unoccupied'
    0x01: 'Occupied'
  remarks: ''
  signed: ''
  type: ENUM
  unit: ''
STR_AD_ID_MODEL_NAME:
  address: '0x061F'
  arithmetic: ''
  description: Model Name
  remarks: appears when using S-NET pro 2 software
  signed: ''
  type: STR
  unit: ''
STR_AD_PRODUCT_MAC_ADDRESS:
  address: '0x061C'
  arithmetic: ''
  description: WiFi Kit MAC Address
  remarks: ''
  signed: ''
  type: STR
  unit: ''
STR_IN_ERROR_HISTORY_FOR_HASS:
  address: '0x461E'
  arithmetic: ''
  description: Structure Type
  remarks: ''
  signed: ''
  type: STR
  unit: ''
STR_OUT_BASE_OPTION:
  address: '0x860A'
  arithmetic: ''
  description: Structure Type
  remarks: ''
  signed: ''
  type: STR
  unit: ''
STR_OUT_REF_CHECK_INFO:
  address: '0x8613'
  arithmetic: ''
  description: Structure Type
  remarks: ''
  signed: ''
  type: STR
  unit: ''
VAR_IN_CAPACITY_VENTILATION_REQUEST:
  address: '0x4302'
  arithmetic: value / 8.5
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: kW
VAR_IN_CHILLER_EXTERNAL_TEMPERATURE:
  address: '0x42C9'
  arithmetic: value / 10
  description: External sensor-Room temperature
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_CHILLER_PHE_IN_P:
  address: '0x42C4'
  arithmetic: (value / 100) * 0.980665
  description: Inlet pressure
  remarks: ''
  signed: 'true'
  type: VAR
  unit: bar
VAR_IN_CHILLER_PHE_OUT_P:
  address: '0x42C5'
  arithmetic: (value / 100) * 0.980665
  description: Outlet pressure
  remarks: ''
  signed: 'true'
  type: VAR
  unit: bar
VAR_IN_DUST_SENSOR_PM10_0_VALUE:
  address: '0x42D1'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_IN_DUST_SENSOR_PM1_0_VALUE:
  address: '0x42D3'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_IN_DUST_SENSOR_PM2_5_VALUE:
  address: '0x42D2'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_IN_ENTHALPY_SENSOR_OUTPUT:
  address: '0x42CF'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: H
VAR_IN_EXT_VARIABLE_DAMPER_OUTPUT:
  address: '0x42D0'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_IN_FAN_CURRENT_RPM_SUCTION1:
  address: '0x429F'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: 'rpm'
VAR_IN_FAN_CURRENT_RPM_SUCTION2:
  address: '0x42A1'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: 'rpm'
VAR_IN_FAN_CURRENT_RPM_SUCTION3:
  address: '0x42A3'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: 'rpm'
VAR_IN_FLOW_SENSOR_CALC:
  address: '0x42E9'
  arithmetic: value / 10
  description: Flow Sensor
  remarks: value appears about every 90 seconds
  signed: 'true'
  type: VAR
  unit: ''
VAR_IN_FLOW_SENSOR_VOLTAGE:
  address: '0x42E8'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_IN_FSV_2011:
  address: '0x4254'
  arithmetic: value / 10
  description: Heating - Outdoor Temp. for WL Max.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_2012:
  address: '0x4255'
  arithmetic: value / 10
  description: Heating - Outdoor Temp. for WL Min.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_2021:
  address: '0x4256'
  arithmetic: value / 10
  description: Heating - Water out Temp. UFH Max.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_2022:
  address: '0x4257'
  arithmetic: value / 10
  description: Heating - Water out Temp. UFH Min.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_2031:
  address: '0x4258'
  arithmetic: value / 10
  description: Heating - Water out Temp. FCU Max.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_2032:
  address: '0x4259'
  arithmetic: value / 10
  description: Heating - Water out Temp. FCU Min.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_2051:
  address: '0x425A'
  arithmetic: value / 10
  description: Cooling - Outdoor Temp. for WL Max.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_2052:
  address: '0x425B'
  arithmetic: value / 10
  description: Cooling - Outdoor Temp. for WL Min.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_2061:
  address: '0x425C'
  arithmetic: value / 10
  description: Cooling - Water out Temp. UFH Max.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_2062:
  address: '0x425D'
  arithmetic: value / 10
  description: Cooling - Water out Temp. UFH Min.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_2071:
  address: '0x425E'
  arithmetic: value / 10
  description: Cooling - Water out Temp. FCU Max.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_2072:
  address: '0x425F'
  arithmetic: value / 10
  description: Cooling - Water out Temp. FCU Min.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_3021:
  address: '0x4260'
  arithmetic: value / 10
  description: DHW - Heat Pump Max. temp.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_3022:
  address: '0x4261'
  arithmetic: value / 10
  description: DHW - Heat Pump Stop
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_3023:
  address: '0x4262'
  arithmetic: value / 10
  description: DHW - Heat Pump Start
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_3024:
  address: '0x4263'
  arithmetic: ''
  description: DHW - Heat Pump Min. Space heating operation time
  device_class: duration
  remarks: ''
  signed: 'false'
  type: VAR
  unit: 'min'
VAR_IN_FSV_3025:
  address: '0x4264'
  arithmetic: ''
  description: DHW - Heat Pump Max. DHW operation time
  device_class: duration
  remarks: ''
  signed: 'false'
  type: VAR
  unit: 'min'
VAR_IN_FSV_3026:
  address: '0x4265'
  arithmetic: ''
  description: DHW - Heat Pump Max. Space heating operation time
  device_class: duration
  remarks: ''
  signed: 'false'
  type: VAR
  unit: 'h'
VAR_IN_FSV_3032:
  address: '0x4266'
  arithmetic: ''
  description: DHW - Booster Heat Delay Time
  device_class: duration
  remarks: ''
  signed: 'false'
  type: VAR
  unit: 'min'
VAR_IN_FSV_3033:
  address: '0x4267'
  arithmetic: value / 10
  description: DHW - Booster Heat Overshoot
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_3034:
  address: '0x4268'
  arithmetic: value / 10
  description: ''
  remarks: not for EHS Mono HT Quiet
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_3043:
  address: '0x4269'
  arithmetic: ''
  description: DHW - Disinfection Start Time
  device_class: duration
  remarks: ''
  signed: 'false'
  type: VAR
  unit: 'h'
VAR_IN_FSV_3044:
  address: '0x426A'
  arithmetic: value / 10
  description: DHW - Disinfection Target Temp.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_3045:
  address: '0x426B'
  arithmetic: ''
  description: DHW - Disinfection Duration
  device_class: duration
  remarks: ''
  signed: 'true'
  type: VAR
  unit: 'min'
VAR_IN_FSV_3046:
  address: '0x42CE'
  arithmetic: value / 60
  description: DHW - Disinfection Max time
  remarks: NASA Value is [minutes], not [hours]
  device_class: duration
  signed: 'false'
  type: VAR
  unit: 'h'
VAR_IN_FSV_3052:
  address: '0x426C'
  arithmetic: value / 0.1
  description: DHW - Forced DHW Operation Time Duration
  device_class: duration
  remarks: ''
  signed: 'true'
  type: VAR
  unit: 'min'
VAR_IN_FSV_3081:
  address: '0x42ED'
  arithmetic: ''
  description: DHW - Energy Metering BUH 1 step capacity
  remarks: ''
  signed: 'true'
  type: VAR
  unit: 'kW'
VAR_IN_FSV_3082:
  address: '0x42EE'
  arithmetic: ''
  description: DHW - Energy Metering BUH 2 step capacity
  remarks: ''
  signed: 'true'
  type: VAR
  unit: 'kW'
VAR_IN_FSV_3083:
  address: '0x42EF'
  arithmetic: ''
  description: DHW - Energy Metering BSH capacity
  remarks: ''
  signed: 'true'
  type: VAR
  unit: 'kW'
VAR_IN_FSV_4012:
  address: '0x426D'
  arithmetic: value / 10
  description: Heating - Heat Pump Outdoor Temp. for Priority
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_4013:
  address: '0x426E'
  arithmetic: value / 10
  description: Heating - Heat Pump Outdoor Heat OFF
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_4014:
  address: '0x426F'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_4024:
  address: '0x4270'
  arithmetic: value / 10
  description: Heating - Backup Heater Threshold Temp.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_4025:
  address: '0x4271'
  arithmetic: value / 10
  description: Heating - Backup Heater Defrost Backup Temp.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_4033:
  address: '0x4272'
  arithmetic: value / 10
  description: Heating - Backup Boiler Threshold Temp.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_4042:
  address: '0x4286'
  arithmetic: value / 10
  description: Heating - Mixing Valve Target Delta Heating
  remarks: ''
  signed: 'false'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_4043:
  address: '0x4287'
  arithmetic: value / 10
  description: Heating - Mixing Valve Target Delta Cooling
  remarks: ''
  signed: 'false'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_4045:
  address: '0x4288'
  arithmetic: ''
  description: Heating - Mixing Valve Control Interval
  device_class: duration
  remarks: ''
  signed: 'false'
  type: VAR
  unit: 'min'
VAR_IN_FSV_4046:
  address: '0x4289'
  arithmetic: value / 0.1
  description: Heating - Mixing Valve Running Time
  device_class: duration
  remarks: ''
  signed: 'false'
  type: VAR
  unit: 's'
VAR_IN_FSV_4052:
  address: '0x428A'
  arithmetic: value / 10
  description: Heating - Inverter Pump Target Delta
  remarks: ''
  signed: 'false'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_5011:
  address: '0x4273'
  arithmetic: value / 10
  description: Outing Mode - Water Out Temp. for Cooling
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_5012:
  address: '0x4274'
  arithmetic: value / 10
  description: Outing mode - Room Temp. for Cooling
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_5013:
  address: '0x4275'
  arithmetic: value / 10
  description: Outing mode - Water Out Temp. for Heating
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_5014:
  address: '0x4276'
  arithmetic: value / 10
  description: Outing mode - Room Temp. for Heating
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_5015:
  address: '0x4277'
  arithmetic: value / 10
  description: Outing mode - Auto Cooling WL1 Temp.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_5016:
  address: '0x4278'
  arithmetic: value / 10
  description: Outing mode - Auto Cooling WL2 Temp.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_5017:
  address: '0x4279'
  arithmetic: value / 10
  description: Outing mode - Auto Heating WL1 Temp
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_5018:
  address: '0x427A'
  arithmetic: value / 10
  description: Outing mode - Auto Heating WL2 Temp
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_5019:
  address: '0x427B'
  arithmetic: value / 10
  description: Outing mode - Target Tank Temp
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_5021:
  address: '0x427C'
  arithmetic: value / 10
  description: DHW Saving - DHW Saving Temp.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_5023:
  address: '0x42F0'
  arithmetic: value / 10
  description: DHW Saving - DHW Saving Thermo on Temp.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_5031:
  address: '0x427D'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_IN_FSV_5032:
  address: '0x427E'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_IN_FSV_5082:
  address: '0x42DB'
  arithmetic: value / 10
  description: PV Control - Setting Temp. Shift Value (Cool)
  remarks: ''
  signed: 'false'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_5083:
  address: '0x42DC'
  arithmetic: value / 10
  description: PV Control - Setting Temp. Shift Value (Heat)
  remarks: ''
  signed: 'false'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_5092:
  address: '0x42DD'
  arithmetic: value / 10
  description: Smart Grid Control - Setting Temp. Shift Value (Heat)
  remarks: ''
  signed: 'false'
  type: VAR
  unit: "\u00b0C"
VAR_IN_FSV_5093:
  address: '0x42DE'
  arithmetic: value / 10
  description: Smart Grid Control - Setting Temp. Shift Value (DHW)
  remarks: ''
  signed: 'false'
  type: VAR
  unit: "\u00b0C"
VAR_IN_MCC_GROUP_MAIN:
  address: '0x42B2'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_IN_MCC_GROUP_MODULE_ADDRESS:
  address: '0x42B1'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_IN_MCC_MODULE_MAIN:
  address: '0x42B3'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_IN_MODULATING_FAN:
  address: '0x42CC'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_IN_MODULATING_VALVE_1:
  address: '0x42CA'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_IN_MODULATING_VALVE_2:
  address: '0x42CB'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_IN_SENSOR_CO2_PPM:
  address: '0x421B'
  arithmetic: ''
  description: CO2 sensor detection ppm
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_IN_TEMP_ELECTRIC_HEATER_F:
  address: '0x4207'
  arithmetic: subtract 55
  description: Electric heater temperature value
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_TEMP_EVA2_IN_F:
  address: '0x42C2'
  arithmetic: value / 10
  description: Indoor Eva2 In temperature
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_TEMP_EVA2_OUT_F:
  address: '0x42C3'
  arithmetic: value / 10
  description: Indoor Eva2 Out Temperature
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_TEMP_MIXING_VALVE_F:
  address: '0x428C'
  arithmetic: value / 10
  description: Hydro_MixingValve
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_TEMP_PANEL_AIR_COOL1_F:
  address: '0x42A5'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_TEMP_PANEL_AIR_COOL2_F:
  address: '0x42A6'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_TEMP_PANEL_AIR_HEAT1_F:
  address: '0x42AB'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_TEMP_PANEL_AIR_HEAT2_F:
  address: '0x42AC'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_TEMP_PANEL_ROOM_COOL1_F:
  address: '0x42A7'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_TEMP_PANEL_ROOM_COOL2_F:
  address: '0x42A8'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_TEMP_PANEL_ROOM_HEAT1_F:
  address: '0x42AD'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_TEMP_PANEL_ROOM_HEAT2_F:
  address: '0x42AE'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_TEMP_PANEL_TARGET_COOL1_F:
  address: '0x42A9'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_TEMP_PANEL_TARGET_COOL2_F:
  address: '0x42AA'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_TEMP_PANEL_TARGET_HEAT1_F:
  address: '0x42AF'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_TEMP_PANEL_TARGET_HEAT2_F:
  address: '0x42B0'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_TEMP_TARGET_ZONE2_F:
  address: '0x42D6'
  arithmetic: value / 10
  description: Zone2 Room Set Temp.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_TEMP_WATER_IN2_F:
  address: '0x42CD'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_TEMP_WATER_LAW_F:
  address: '0x427F'
  arithmetic: value / 10
  description: Hydro_WaterLawTargetF
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_TEMP_WATER_LAW_TARGET_F:
  address: '0x4248'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_TEMP_WATER_OUT2_F:
  address: '0x4239'
  arithmetic: value / 10
  description: Hydro_HeaterOut
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_TEMP_WATER_OUTLET_TARGET_ZONE2_F:
  address: '0x42D7'
  arithmetic: value / 10
  description: Water Outlet2 Set Temp.
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_TEMP_WATER_OUTLET_ZONE1_F:
  address: '0x42D8'
  arithmetic: value / 10
  description: Zone1 WaterOut Temp
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_TEMP_WATER_OUTLET_ZONE2_F:
  address: '0x42D9'
  arithmetic: value / 10
  description: Zone2 WaterOut Temp
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_IN_TEMP_ZONE2_F:
  address: '0x42D4'
  arithmetic: value / 10
  description: Idiom_RoomTemp_Zone2
  remarks: 'Room temperature for zone #2'
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_OUT_COMP_FREQ_RATE_CONTROL:
  address: '0x42F1'
  arithmetic: ''
  description: ''
  remarks: undocumented, taken from Pyton code
  signed: ''
  type: VAR
  unit: ''
VAR_OUT_CONTROL_DSH1:
  address: '0x827A'
  arithmetic: value / 10
  description: Just for EHS HTU
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_OUT_CONTROL_IDU_TOTAL_ABSCAPA:
  address: '0x82A8'
  arithmetic: value / 8.5
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: ''
VAR_OUT_CONTROL_REFRIGERANTS_VOLUME:
  address: '0x824F'
  arithmetic: value / 10
  description: Refrigerant amount
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_OUT_ERROR_CODE:
  address: '0x8235'
  arithmetic: ''
  description: HTU error code
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_OUT_HIGH_OVERLOAD_DETECT:
  address: '0x82F5'
  arithmetic: ''
  description: PFCM#1 element temperature
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_OUT_INSTALL_COMP_NUM:
  address: '0x8202'
  arithmetic: ''
  description: Number of outdoor unit compressors
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_OUT_INSTALL_COND_SIZE:
  address: '0x82AF'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_OUT_LOAD_EVI_SOL_EEV:
  address: '0x82FC'
  arithmetic: ''
  description: EVI SOL EEV
  remarks: ''
  signed: 'true'
  type: VAR
  unit: ''
VAR_OUT_LOAD_MCU_HR_BYPASS_EEV:
  address: '0x82E8'
  arithmetic: ''
  description: MCU HR Bypass EEV opening diagram
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_OUT_MCU_CHANGE_OVER_EEV1:
  address: '0x826E'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_OUT_MCU_CHANGE_OVER_EEV2:
  address: '0x826F'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_OUT_MCU_CHANGE_OVER_EEV3:
  address: '0x8270'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_OUT_MCU_CHANGE_OVER_EEV4:
  address: '0x8271'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_OUT_MCU_CHANGE_OVER_EEV5:
  address: '0x8272'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_OUT_MCU_CHANGE_OVER_EEV6:
  address: '0x8273'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_OUT_MCU_SENSOR_SUBCOOLER_IN:
  address: '0x826B'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_OUT_MCU_SENSOR_SUBCOOLER_OUT:
  address: '0x826C'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_OUT_MCU_SUBCOOLER_EEV:
  address: '0x826D'
  arithmetic: ''
  description: ''
  remarks: ''
  signed: 'false'
  type: VAR
  unit: ''
VAR_OUT_PRODUCT_OPTION_CAPA:
  address: '0x82E3'
  arithmetic: value / 10.0
  description: Outdoor unit product option capacity (based on 0.1Kw) for EHS
  remarks: ''
  signed: 'false'
  type: VAR
  unit: kW
VAR_OUT_SENSOR_PFCM1:
  address: '0x82E9'
  arithmetic: value / 10
  description: PFCM#1 element temperature
  remarks: Min -54, Max 3000
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_OUT_SENSOR_PIPEIN1:
  address: '0x825F'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_OUT_SENSOR_PIPEIN2:
  address: '0x8260'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_OUT_SENSOR_PIPEIN3:
  address: '0x8261'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_OUT_SENSOR_PIPEIN4:
  address: '0x8262'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_OUT_SENSOR_PIPEIN5:
  address: '0x8263'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_OUT_SENSOR_PIPEOUT1:
  address: '0x8264'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_OUT_SENSOR_PIPEOUT2:
  address: '0x8265'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_OUT_SENSOR_PIPEOUT3:
  address: '0x8266'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_OUT_SENSOR_PIPEOUT4:
  address: '0x8267'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_OUT_SENSOR_PIPEOUT5:
  address: '0x8268'
  arithmetic: value / 10
  description: ''
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_OUT_SENSOR_SUCTION3_1SEC:
  address: '0x82F9'
  arithmetic: value / 10
  description: Suction3 temperature
  remarks: ''
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
VAR_OUT_SENSOR_TOTAL_SUCTION:
  address: '0x82E7'
  arithmetic: value / 10.0
  description: Total Suction Sensor
  remarks: Min -41, Max 150
  signed: 'true'
  type: VAR
  unit: "\u00b0C"
NASA_EHSSENTINEL_TOTAL_COP:
  address: '0x9997'
  arithmetic: ''
  description: Total COP of lifetime
  remarks: Custom Measurment
  state_class: measurement
  signed: 'true'
  type: VAR
  unit: ''
NASA_EHSSENTINEL_COP:
  address: '0x9998'
  arithmetic: ''
  description: Current COP
  remarks: Custom Measurment
  state_class: measurement
  signed: 'true'
  type: VAR
  unit: ''
NASA_EHSSENTINEL_HEAT_OUTPUT:
  address: '0x9999'
  arithmetic: ''
  description: Current generated Heat Output
  remarks: Custom Measurment
  state_class: measurement
  signed: 'true'
  type: VAR
  unit: "W"